What is a GFCI Outlet and Where Do They Go?
We’ve been asked by homeowners: What is a GFCI outlet and where do they go? (or why do we need them?) GFCI stands for Ground Fault Circuit Interrupter. These are also referred to as GFIs, or Ground Fault Interrupters. A GFCI precisely monitors the balance of electrical current moving through a circuit. If the power goes where it shouldn’t, like in a short, the GFCI immediately cuts off the electricity.
A GFCI prevents fatal electrical shocks through the elimination of sustained current draw when a short occurs. This is very different from Arc Fault circuit breakers or Arc Fault Circuit Interrupters (AFCI) which track down and disable slow electrical “leaks” like those incurred from puncturing a wire in a bedroom wall.
About Ground FaultsA ground fault represents any electric path between a source of current and a grounded surface. A ground-fault occurs when current “leaks” and escapes to the ground. How this occurs is significant. If your body provides a path to the ground for this leakage, you could be injured, burned, severely shocked, or electrocuted. Since water conducts electricity so well, ground-faults occur more frequently in areas near water. Water provides a conduit for electricity to “escape” and find an alternate path to the ground.
Water and electricity do not mix, and there are many places in the home and outside where the two exist in close proximity. All switches, sockets, breakers, and circuits for those rooms and areas of the home should be GFCI-protected for your family’s safety. What is a GFCI outlet? It may be the very thing that keeps your family safe in the event of a tragic electrical mishap.
Types of GFCI Devices
While you may have come here asking what is a GFCI outlet, there are actually three basic types of GFCI devices:
The most common GFCI in residential homes comes in a receptacle. This inexpensive device replaces a standard receptacle (outlet). Completely compatible with any standard outlet, it can protect other outlets “downstream” (any outlet receiving power from the GFCI outlet). GFCI outlets are typically “fatter” than standard outlets and take up more space in a single gang or double gang electrical box. Newer technology like the Leviton SmartlockPro Slim GFCI take up far less space than ever before. Wiring a GFCI outlet is no big deal, but you need to do it correctly in order for the protection to be effective.
Circuit Breaker Type
This type of GFCI is becoming more and more popular since it allows builders and electricians to use standard (inexpensive) outlets and simply wire the entire circuit with a single GFCI circuit breaker installed in the panel box. These breakers have the advantage of protecting every fixture on the circuit—lights, outlets, fans, etc. They also provide protection against overloads and simple short-circuits.
This is an outlet strip or other device providing GFCI-level protection in a portable unit.
Where to Install GFCIs
Since around 1973, GFCI is required for most outdoor receptacles in homes built to comply with the National Electrical Code. In 1975 that was extended to bathroom receptacles and in 1978 garage wall outlets were added. It took until around 1987 for the code to include kitchen receptacles. Many homeowners find themselves redoing their electrical to comply with current law. All receptacles in crawl spaces and unfinished basements also require GFCI outlets or breakers (since 1990).
Obviously, newer GFCI circuit breakers make retrofitting a home with GFCI protection much easier than replacing each individual outlet in a system, especially if you aren’t sure about your wiring for a given room. For homes protected by fuses (seriously consider upgrading your box), you are going to have to stick to GFCI receptacles. Focus on the most critical areas like bathrooms, kitchens, crawl spaces, and outdoor areas.
We have a separate article on wiring a GFCI outlet, but most savvy consumers can do it themselves if they follow the instructions. Just make sure to completely disable the breaker before you begin. To test the GFCI receptacle after installation, plug something into the outlet (like a radio or light) and turn it on. Press the “TEST” button on the GFCI to ensure the “RESET” button pops out, and the device turns off. If the “RESET” button pops out, but the light does not go out, the GFCI has been wired improperly. If the “RESET” button does not pop out, the GFCI is defective and should be replaced. Pressing the “RESET” button re-activates your circuit. You can also purchase inexpensive GFCI-compatible circuit testers.
There…Not Too Difficult, Right?
Ground Fault Circuit Interrupters should exist in any home. When rewiring or updating your house to bring it up to code, pay attention to where to place GFCI outlets or breakers. This inexpensive product can provide an incredibly beneficial level of safety for your family.